Features and Construction
The Rosenberg Centrifugal Fans with a free-running impeller of the range DKN_ were designed for installation in appliances such as Air Handling Units (AHU), hygienic- and clean room filter units. During the development of this unit with backward-curved impeller without scroll casing, special attention was paid to optimize the efficiency over a wide characteristic curve having at the same time high performance and an optimum sound power level. The fans are suitable to handle air and other non-aggressive gases or fumes. The motors are available with latest three-phase IEC standard motors or standard NEMA Premium Efficiency motor. Moreover, different features depending on the application such as explosion proof or for hazardous locations etc. are available. Depending on fan construction, the following two fan types are available: DKND and DKNM
Fan module with mounting stand.
Inlet cone is mounted and adjustable to correct depth.
Complete unit installable with vibration dampers or springs.
Fan with NEMA PE motor, respectively with IEC standard motor; type IMB3.
Fan module without mounting stand.
Inlet cone is mounted and adjusted to correct depth.
Fan with NEMA PE motor, resp. with IEC standard motor, type IMB5.
Advantages of radial fans with a free-running impeller
- Easy maintenance as a result of no fan belt abrasion or wear and tear
- Hygienic, easy to clean
- Can be installed either with a horizontal or vertical shaft (DKNB; DKNM)
- Compact, space-saving construction
- Easy determination of the airflow due to measuring device
- Technical decoupling of vibration of the module possible
- High economic efficiency as a result of the optimized efficiency of the impeller
The impellers with 7 backward curved blades are made of aluminum (AIMg3) and are statically and dynamically balanced with hubs according to quality level G6.3 DIN ISO 1940.
The impellers can be supplied with special coating for harsh environments if needed.
Direction of rotation
Direction of rotation of the impellers (viewed from the inlet side) is clockwise.
Wrong direction of rotation can overload the motor; therefore it is essential to check the direction of rotation before initial operation.
The inlet cones are made of galvanized sheet steel.
They are fluidic optimized and offer a good airflow of the impeller.
The optimal immersion depth of the impeller is shown on the according to dimensional drawings.
Airflow control and monitoring can be done through a circular lead on the inlet cone.
Rosenberg’s DKNM and DKNB fans are equipped with NEMA Premium Efficiency motors, 230V/460V/60Hz.
They can be supplied with the following options: partially or totally enclosed, explosion proof, etc. Different voltages are available as well as with a different number of poles for different nominal speeds. Further information on the drive motor, motor safety, and speed control can be found in the individual special description of each ventilator type.
The wiring box of the motor is easily accessible. The motor has to be connected according to the wiring diagram and in accordance with valid regulations and local laws.
In case of operation with frequency transformer, please refer to the operation manual.
The installation specific optimal adjustment for the required operating point can only be released with a suitable speed control system. The speed is changed by changing the frequency with a frequency converter. The maximum frequency of the motor must be observed. At higher frequencies than fmax, the motor will thermally overload and the temperature sensor will react after a certain period of heating up. The cut-off frequency adjustable on the frequency converter is 50Hz for IEC standard motors and 60Hz for NEMA motors. In case of emergency service or failure of the frequency converter, all fans can be operated at 400V, 50Hz, respectively 460V, 60Hz, main supply. When the motors are operated by a frequency converter, the maximum speed of voltage increase of 500V/μs should not be exceeded.
Depending on the type of frequency converter, and the length of the cable between motor and frequency converter, additional components must be provided (e.g. a sinus filter).Description of constructions: